Residential Wiring - The Right Way!
|Wiring Done Right|
Got Questions? Get Answers! Ask the Experts on EZ-Forum
Social Media Links
Help spread our popularity, get the word out.
Read the legal disclaimer page - click the legal link in the menu at bottom of page
There is very few circumstances in which multiple switches in series would be desired.
Switches wired in series require all switches to be in the on position for the circuit to be on, when any one switch is off the circuit is off regardless of the position of the other switch.
Now at the moment I think of one possible usage for this, and that is for a cut off switch for the furnace, this switch is often labeled with the 'ON' position on the faceplate. In an emergency you want without a doubt know where the off position is. If you desire a cut off in two different locations 3 way switches is not the answer as there is no definitive position of 3 way switches as to off and on. If you wire two basic switches wired in series you can position these switches so that on is always with the switch up and off is always with the switch down, both switches must be on for the circuit to be on.
those that live where the new 2011 NEC code is in effect, please read
Since I could never imagine anyone using a series type circuit switch wiring for lighting loads I have not created specific wiring sequences for series switch wiring that meet this new NEC rule, but just for your information the 'power source and switched feed on different switch' would be the only option that I provided that would meet the new rule criteria.
Two switches wired in series options....
|Power Source at Switched Item|
|Power Source and Switched Feed at Same Switch|
|Power Source and Switched Feed at Different Switch|
Written: Dec. 22. 2011
Revised: June 30, 2013
Proof Read / Released: July 10,2013
By: Donald Kerr
Contact Us / Creator / Forums / Legal
Copyright 2014 +
All Rights Reserved
Donald Kerr / Wiring Done Right
Back to Top