Don't let your house
go up in Flames!
Get it Right the First time!
Residential Wiring - The Right Way!
Electrical Wiring and Safety
Social Media Links
Help spread our popularity, get the word out.
Main Electrical Panel
WHILE EXTREME CARE HAS BEEN IMPLEMENTED IN THE PREPARATION OF THIS SELF-HELP DOCUMENT, THE AUTHOR AND/OR PROVIDERS OF THIS DOCUMENT ASSUMES NO RESPONSIBILITY FOR ERRORS OR OMISSIONS, NOR IS ANY LIABILITY ASSUMED FROM THE USE OF THE INFORMATION, CONTAINED IN THIS DOCUMENT, BY THE AUTHOR and / OR PROVIDER.
Read the legal disclaimer page - click the legal link in the menu above
The main electrical panel can also be called the electrical service panel or electrical distribution panel and is where all wiring through out the home connect.
Power lines coming from your local electrical company come in from the pole transformer to a mask on the home or they may come in from underground routing.
The meter mount is a mounting terminal bridging through the meter to the wire that connect to the main cut off inside the home. The purpose of the electrical meter is to measure the amount of power consumption that is utilized in the home for purposes of determining how much your electrical bill will be.
This meter is usually mounted close to where the main electrical wires will enter the home and inside there must be a main electrical cut off located close to this electrical entrance.
Now quite often the main electrical cut-off for the home is part of the main electrical distribution panel, but it can be separated but close by as a separate entity from the panel with the breakers or fuses in it. The purpose of the main cut-off is to shut down electricity beyond which is before the main distribution breaker or fuses, in other words being able to shut off the electricity to all circuits to the entire home.
Most homes that have basements the main cut-off and
distribution panel will be located in the basement of the home.
There is code rules that require the area around the main cut-off /
distribution / electrical panel be clear of clutter, there is also rules
relating to minimum distance from water sources. The main electrical cut
off in modern homes is in the form of a main cut off breaker will
provides not only a shut down switch but over current protection rated
at whatever your electrical service is which could be 200 amps.
Common power service to home can be anywhere from 60 amps to 200 amps, 200 amp service seems fairly common in modern homes.
Now the average homeowner is not going to be installing a new main service panel unless the person has above average knowledge meaning you would likely be working in the electrical field. Replacing a main electrical service panel that also includes the main breaker cut off would mean that you would need the utility company to help in order to cut off the power prior (on the utility side of the main breaker cut off) to the main breaker cut off, leave such a major job to a qualified professional electrician.
We will now dissect a modern the electrical service / distribution panel.
When working with an existing panel (assuming the panel was originally installed by a professional) it should be easy to just look and see the correct bus bar where the grounded conductors (neutrals) [white wires] are connected to, and where all the bare equipment wires are going to, so if adding a new breaker put the wire white (neutral) to the same bus bar where the other white wires are going and the same hold true to where the bare wires are going to. The ungrounded conductors (hots - usually red or black) attach to the breaker itself.
Now there are specialized breaker items such as surge protectors that require a neutral connection or ground coming to it, so make sure you do not follow that as neutrals from circuit cables go to a separate bus bar it should be easy to find.
Bellow is a 3 part video I found posted on you tube that does a good explanation of the main electrical panel.
Some comments about the videos.
1. I would prefer when working in a live electrical panel to be using better insulated screwdrivers, ones with insulated stems.
2. For greater safety - the electrical safety authority is now recommending using only multi meters with fused leads (link will open in new tab / window)...
3. In the panel that is illustrated in the videos the mains coming in from the street are aluminium with an anti-oxidant pasted on the connected ends / internal circuits where copper wired.
4. Although many have done work in a live main panel carefully without wearing insulated electricians gloves, I would highly recommend using them.
5. At one spot in the video he mentions the word positive in regards to the hot wire, in AC (alternating current) there is no + or - dedicated wire, AC is alternating 60 times (60 hertz) a second, some countries use a 50 hertz AC standard. You have a ungrounded conductor (hot) which for the United States and Canada most times is red or black; a grounded conductor (neutral) usually white in color; and an equipment grounding conductor which is either bare or green.
We have experts that work in the field on our forums so please take advantage of that for further clarification and questions.
Written: March 12, 2012
Copyright 2014 +
All Rights Reserved
Donald Kerr / Wiring Done Right